Toggle mobile menu
Free Shipping on Select Products!
Decay Test Results
110V/220V, Testing Voltage: 1kV to 100V
Installation: The SL-1104 is an
overhead unit designed to provide ideal coverage for control
of electrostatics. Note: Do not insert objects into air
intake or outlet grille and do not operate the SL-1104 in
inflammable or explosive environments. The SL-1104 ionizer
should be affixed 24 to 54 inches above the work surface
with center targeted directly over work area. This unit may
also be positioned and operated vertically should conditions
dictate. Avoid drafty locations such as that caused by air
conditioning, heater outlets, etc
Attachment to overhead supports: S hooks and chains may be used for mounting these ionizers to structurally sound ceilings or wire shelves. Chains and mounting hardware should have a minimum safe working load of at least 50 pounds. When mounting the unit to ceilings it is important to check state and local codes to insure compliance. These units are typically hung in the same fashion as an overhead light fixtures (independently attached to the overhead building superstructure). Attachment to suspended ceilings only are typically not compliant with local codes. Mounting to workbench overhead supports: These ionizers may be mounted to work bench overhead shelves and beams using the supplied side mounting bracket in conjunction with angle iron, bolt on L brackets etc. These ionizers may be used either horizontally or vertically.
The SL-1104 requires 110VAC /60Hz (standard) or 220VAC /
50Hz (optional) power. These units must be grounded. Each
unit is supplied with standard US 3 prong male grounded
power plug (standard). Do not modify the plug or use an
ungrounded 3 prong receptacle. If an extension cord is
required use heavy gauge fully grounded cords only.
Activate the SL-1104 overhead ionizing blower by turning the
fan speed knob clockwise. The ionization indicator will
illuminate and indicate the presence of ionized air.
Airflow speed may easily be adjusted from 3% to 100% output
utilizing the fan speed knob. The time required to
neutralize electrostatic potential is dependent on the
distance of ionizer to work surface, the voltage collected
on the insulator and the speed of fans. When used in
electronic assembly the ionized air stream should cover as
much of the working area as possible. The constant flow of
ionized air prevents items from developing an electrostatic
potential and neutralizes electrostatic charges present on
objects introduced to the airflow.
Clean emitters points as needed. Inspect the points on
occasion using a flashlight and magnifying glass. The points
should be sharp and free of carbon build up and residues. To
clean the ion emitter points press and turn the emitter
cleaner knob (located in the center of each air outlet)
clockwise one full turn and release the knob. The emitter
points should always be sharp and not rounded at the point.
Should these tips become rounded simply replace the emitter
Please Note: The typical emitter life is greater
than 4 years.
Replacement emitters rings are easy to
install and available from United SCP. Periodically test the
ionic output as indicated by your internal ESD program or
ANSI/ESD S 20.20-2014, TR53, Air Ionizer Compliance
Verification (discharge time and offset voltage).
Max 1.66 Amp (fan
Min 0.83 Amp (fan
46.5" (L) x 6.10" (W)
x 4.33" (H) inches
speed low: 180 CFM
speed high: 440 CFM
Flow amount equals sum of four fan